KNX devices are protected internally against overvoltage impulses up to 2 kV (1.2/50). The overvoltage protector is used to protect them beyond this level. It takes the form of a one-part blue bus terminal with three fixed core wires.
To install the overvoltage protector, the blue bus terminal is inserted in place of the usual bus terminal. The red and the black core wires are connected to the bus cable and the green/yellow wires are connected to the nearest earthing point (e.g. protective conductor). In the distribution board, the overvoltage protector can also be connected via a data rail connector.
- Rated Voltage: 24VDC
- Rated Current: 6A
- Rated Discharge Current: 5kA
- Protection Level: 350mA
- Earth Connection: .75mm2
|Operating voltage||KNX Bus (29VDC)|
|EAN||40 16779 00570|