KNX Interface for Fujitsu General Limited Air Conditioners
Simple installation. Can be installed inside the own AC indoor unit, connecting one side directly to the BWR bus, and the other side directly to the KNX TP-1 (EIB) bus.
Configuration is made directly from ETS, the database of the device comes with a complete set of communication objects allowing, from a simple and quick integration using the basic objects, to the most advanced integration with monitoring and control all the AC units parameters. Also available specific devices communication objects, as save and execute scenes.
Four binary inputs for potential-free contacts provide the possibility to integrate many types of external devices. Also configurable from ETS, they can be used for switching, dimming, shutter/blind control, and more.
Allows the use of a KNX temperature sensor for the air conditioning control.
IntesisBox FJ-RC-KNX-1i will offer you a full integration of the air conditioning in your KNX projects at a very affordable price.
- Bus Voltage: KNX Bus 21...30VDC
- Bus Current Consumption: 7mA
- AC Indoor Unit Bus: 13-18V
- AC Indoor Bus Current: 80mA
- Inputs: 4 x Potential Free
|Operating voltage||KNX Bus (29VDC)|