Radio Module for Smoke Alarm Device Dual
Radio module for the wireless connection of smoke alarm device Dual Q.
Downwards-compatible, therefore it can also be used for smoke alarm device Dual/VdS.
If one smoke alarm device detects a fire, all assigned smoke alarm devices sound the alarm.
The radio module is plugged in at the interface of the smoke alarm device Dual. The networking terminals of the smoke alarm device can continue to be used when the module is attached. This allows combined lines to be set up (wired or via radio).
Due to the compatibility to the radio bus system, alarm messages can be used to control the radio actuators. This can be used for example to switch on the light or run up blinds in the case of an alarm.
With a radio remote control or wall transmitter, the smoke alarm device can be muted following an alert of approx. 10 minutes. If another networked smoke alarm device triggers an alarm during this time, e.g. via the 2-wire cable or radio transmission, the smoke alarm device outputs an alert despite muting.
Controlling eNet components can only be realised on eNet in connection with the radio transformer.
Please observe the planning information in the Technical Appendix.
The battery can not be purchased from Gira as a spare part.